Power Control Center Panel ( PCC ) / Suppliers and Exporters
These panels are manufactured from 14/16 SWG CRCA material semi bolted structure firmly supported. It Ensures desired breaking capacities, temperature rise & IP protection. This allows space for incoming & outgoing Cable termination. All starters are Type Two Co-ordinated. CT terminals, Outgoing terminals are stud type as standard practice. Our Panel board also offers Cable Alley Illumination Lamp, Space Heaters with Thermostats
MCC/PCC/ DB Specification :
CONSTRUCTIONAL FEATURES : Power Control Center Panel MCC panel design is robust and firmly constructed to suit a wide range of industries and buildings. The supporting structures are made up from 2.0 mm thickness steel sections, punched, fully pressed by CNC machines. The door covers, partitions and panel parts are fabricated with CNC machines for high precision and accuracy. Base degree of protection is IP42. Higher degree of protection like IP54 or more can be manufactured on request. Samcon switchboards can be supplied both with top and or bottom entry.
All metal parts undergo thorough chemical treatment for epoxy powder adhesion and anti-rust to ensure high quality finishing. As standard, epoxy powder coating of 70 micron is applied evenly on all metal surface and oven baked at an average temperature of 150°C. Samcon pays great attention to the standard of workmanship and finishes.
Non-insulated or insulated high conductivity copper/Aluminum busbars with neutral are housed at the top section of the cubicle. The main busbars are mounted and supported on SMC busbar supports. The busbar chamber is housed in a separate compartment on top of the cubicle with facilities for segregation. Maximum temperature rise is less than 70°C on an ambient of 40°C.
INTERNAL SEPARATIONS OF ASSEMBLIES (FORM 1, 2, 3 AND 4) : Samcon switchboard can be provided with partitions for protected spaces according to Form 1 to Form 4. The form of separation according to the latest IEC60439-1:1999 offers an internal protection of minimum IP2X or more.
Wiring : Entire wiring is done with high grade bright copper annealed standard PVC or FRLS or HR FR insulated flexible wires. All doors are earthed with the help of 1.5 sqmm yellow green wire. C DC wiring is done with 2.5 / 1.5 sqmm white wire. ontrol wiring is carried with minimum 1.5 sqmm Gray wire & CT wiring is done with 2.5 sqmm Gray wires. . Electronic Card signal wiring is done with 1 sqmm Shielded wire.
Cable Chamber : Adequate sized cable Chamber of is provided on the side of Each Vertical alongwith enough number of Cable Tie bars. The identification markers & feeder designation sticker are provided with terminal block. Control & Power TB’s are separated from each other. Each Cable Chamber is supplied with panel illumination CFL lamp with door switch & heater & Thermostats can also be supplied optionally.
Component Identification : To ease the wire routings, all the base plates are neatly mounted with necessary electrical components & wherever necessary PVC Trufs are provided. Both on the components & base plates, the component Identification stickers are provided .
before starting the manufacturing of PCC/MCC of the panel, following Drawings are provided to the customer
a) General Arrangement
b) Single Line Diagram
c) Bill Of Material
d) General Notes
e) Control Circuits
After manufacture & testing of panel as built diagram are provided.
a) Dimensional Check
b) Bill of Material Verification
c) Functional Checks
d) Relay Function Test( On case to Case basis)
e) Insulation resistance test
f) High Voltage Test 2.5. KV for 1 minute
These Tests can be witnessed by the customer